誘導電動機の発電確認と単独運転検出装置への影響について About the Power Generation Confirmation of the Induction Motor and the Influence on the Islanding Detection Device
The photovoltaic generation system must have protection device and islanding detection devices to connect with utility line of the electric power company. It is regulated in the technological requirement guideline and the electric equipment technology standard that the country provides. The islanding detection device detected purpose install for blackout due to the accident occurrence of the earth fault and the short-circuit in the utility line. When the islanding detection device detects the power blackout, it is necessary to stop the photovoltaic generation system immediately. If the photovoltaic generation system is not stopped immediately, electricity comes to charge the utility power line very at risk. We had already known that the islanding detection device can't detect the islanding phenomenon, if is there the induction motor in the loads. Authors decided to investigate the influence that the induction motors gave to the islanding detection device. The result was the load condition that the induction motors changed generator the voltage is restraining. Moreover, it was clarified that the time of the islanding was long compared with the load condition of not changing into the state of the generator. The value changes into the reactance of the induction motors according to the frequency change after the supply of electric power line stops. The frequency after the supply of electric power line stops changes for the unbalance the reactive power by the effect of the power rate constancy control with PLL of the power conditioner. However, the induction motors is also to the changing frequency, makes amends for the amount of reactive power, and the change in the frequency after the supply of electric power line stops as a result is controlled. When the frequency changed after the supply of electric power line stopped, it was clarified of the action on the direction where it made amends from the change of the constant for the amount of an invalid electric power, and the possession of the characteristic in which the continuance of the individual operation was promoted.
- 電気学会論文誌. B, 電力・エネルギー部門誌 = The transactions of the Institute of Electrical Engineers of Japan. B, A publication of Power and Energy Society
電気学会論文誌. B, 電力・エネルギー部門誌 = The transactions of the Institute of Electrical Engineers of Japan. B, A publication of Power and Energy Society 128(7), 967-975, 2008-07-01
The Institute of Electrical Engineers of Japan